CAFCO® 400 AC is a gypsum based medium density Wet Mix Spray-Applied Fire Resistive Material (SFRM) designed to provide protection for structural steel in commercial and high rise construction areas which may be subjected to higher levels of abuse such as mechanical and electrical rooms or elevator shafts.
CAFCO 400 AC offers enhanced strength, durability and excellent fire protection and meets the current IBC bond strength requirement of ≥ 430 psf for buildings over 75 ft. in height and 1000 psf for buildings over 420 ft. in height.
CAFCO 400 AC’s physical properties, combined with superior fire resistive performance and application efficiencies, make it the ideal choice for high rise structures and interior conditioned environments.
- Offers the most cost effective fire resistance performance per unit thickness and greatest productivity of any medium density SFRM.
- Less material is needed to achieve required fire ratings.
- Provides added value as a thermal insulator.
- Meets current IBC bond strength requirements for building over 420 ft. in height.
- Meets or exceeds all major fire protection specifications for commercial structures including ANSI/UL 263 and ASTM E119.
- Offers LEED building credits for recycled content.
Designed to provide fire protection for up to 4 hour ratings to various floor and roof deck assemblies, steel beams, columns, and joists in commercial construction projects.
Fire Tests & Approvals
In order to meet the performance and durability criteria set forth by the American Institute of Architects (AIA) and other major industry specifying organizations, CAFCO® 400 AC has undergone the most rigorous testing in accordance with the world’s most demanding safety protocols.
- Cellulosic – ANSI/UL263 (ASTM E119) – Fire Tests of Building Construction and Materials
- UL Classification Mark
- Evaluation Service Report
- Major Specification and Approval Compliance
Cellulosic – ANSI/UL263 (ASTM E119) – Fire Tests of Building Construction and Materials
This cellulosic fire test is traditionally used to evaluate materials for use in the protection of modern day commercial structures. This test reaches 1000°F (537°C) after 5 minutes and gradually reaches a temperature of 2000°F (1093°C) after a period of up to 4 hours.
CAFCO 400 AC is classified by Underwriters Laboratories for up to 4 hours protection in accordance with ANSI/ UL263 and is listed within various UL Designs.
UL Classification Mark
The UL Classification Mark indicates compliance with global requirements as it relates to a specific risk or casualty. With the Classification service, UL determines that a manufacturer has demonstrated the ability to produce a product complying with UL’s requirements with respect to one or more of the following:
- Specific risk, e.g., casualty, fire, etc.
- Performance under specific conditions
- Compliance with regulatory codes
- Compliance with specific standards such as international standards
- Other condition, as determined by UL
All of the products carrying a UL Classification Mark are covered by UL’s Follow-Up Services program to verify that products carrying the UL Classification Mark continue to be manufactured in compliance with UL’s safety requirements.
Major Specification and Approval Compliance
CAFCO 400 AC complies with the requirements of the following specifications:
- MasterSpec®, Section 078100 Applied Fireproofing (AIA)
- MasterFormat® 2014, Section 07 81 00 Applied Fireproofing (CSC,CSI)
- Unified Facilities Guide Specification, UFGS 07 81 00
- Spray-Applied Fireproofing (USACE, NAVFAC, AFCEC, NASA)
- Master Construction Specifications, Number 07 81 00
- Applied Fireproofing (VA)
- Code of Federal Regulations, Title 40 Protection of the Environment (EPA)
- PBS-P100, Facilities Standards for the Public Buildings Services (GSA)
|ASTM Physical Performance Standards||Test Performance* Spray-Applied Fire Resistive Materials (SFRM’s)|
|Physical Property||ASTM Standard||Industry Performance Requirements||CAFCO 400 AC|
|Surface Burning Characteristics||ASTM E84||Flame Spread: 10 or less
Smoke Developed: 0
|Density||ASTM E605||22 pcf (353 kg/m3)||22-25 pcf (352-400 kg/m3)|
|Cohesion / Adhesion (Bond Strength)||ASTM E736||430 psf (20.6 kPa)||1,849 psf (88.5 kPa)|
|Deflection||ASTM E759||No cracks, spalling, or delamination||No cracks, spalling, or delamination|
|Bond Impact||ASTM E760||No cracks, spalling, or delamination||No cracks, spalling, or delamination|
|Compressive Strength||ASTM E761||7,344 psf (351.7 kPa)||8,719 psf (417.5 kPa)|
|Corrosion||ASTM E937||Does not promote corrosion of steel||Does not promote corrosion of steel|
|Air Erosion||ASTM E859||Max. 0.025 g/ft.2||0.000 g/ft.2 (0.000 g/m2)|
|Fungal Resistance||ASTM G21||Zero Growth After 28 days||Zero Growth After 28 days|
|Thermal Properties||ASTM C518||Conductivity[k] – 0.494 BTU in/hr ft2 oF @ 75oF
(0.0712 W/m•K @ 24oC)Resistance [R/inch]-2.02
*Based on independent laboratory tests under controlled conditions.